Payment & Shipping Terms:
|Rated Input Power:||1012W||Protection Level:||IP55|
|Cover Material:||Galvanized Steel||Installation Mode:||Door Mounted|
|Refrigerant:||R410a||Rated Input Current:||4.6A|
server cabinet air conditioner,
control cabinet air conditioner
Rated Input Power: 1012W 2500W Outdoor Cabinet Air Conditioner Rated Input Current: 4.6A
|Place of Origin: Shenzhen, China (Mainland)m,||Rated Cooling Capacity : 2600W|
|Brand Name: ESTEL||Rated Heating Capacity:300/500W (optional)|
|Model: TC06-250JFH/01(KT044 AC220V 60Hz)||Dimension: H×W×D 850×500×271mm|
|Product Name: Outdoor Cabinet Air Conditioner||Input Voltage: AC220V/60Hz|
|Certification: ISO9001, CE, 3C, FCC, TLC||Rated Input Current: 4.6A|
|Cover: including outer cover (galvanized steel)||Rated Input Power: 1012W|
|Color: grey||Working Temperature: -20°C ~ +55°C|
|Protection Level: IP55||Noise: ≤65dB|
|Installation Mode: door mounted||Refrigerant: R410A|
|Support OEM||Cooling Method: compressor, active cooling|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 set|
|Payment Terms:||T/T, L/C,DA,DP etc|
|Supply Ability:||16,000 sets per month|
|Delivery Time:||7-15 working days|
|Packaging Details:||carton + wooden case + pallet|
(1) Technical Parameters
|Environmental Performance||working environmental temperature||-20°C ~ 55°C|
|storage temperature||-40°C ~ 70°C|
|Thermal Performance||rated cooling capacity||
|rated heating capacity||300W/500W (optional)|
|rated input current||
|rated input power||
Dimension Diagram: H×W×D: 850×500×271mm
TC06-250JFH/01(KT044) Air Conditioner is a kind of cooling product developed for outdoor cabinets. It is applicable for the scenarios where internal equipment of the cabinet emits a large quantity of heat and is sensitive to the environment temperature and where the indoor environment needs to be isolated from the outdoor environment completely. This product has full functions, integrating external fan control function. It features high reliability and easy installation and can work immediately upon power on, avoiding complex adjustment.
The internal cycle air path absorbs hot air from the upside, and discharges cold air from the downside of the air conditioner. The external cycle air path absorbs external cold air from the downside, and discharges hot air from the upside after heat exchange.
The cabinet air conditioner is widely applied in outdoor telecom cabinet, outdoor battery cabinet, small and medium sized telecom room, UPS room, outdoor base station room, etc.
L N PE : power supply port (voltage input: 220VAC±15% 60Hz)
F+ F- : direct ventilation output port
AL1 AL2: general alarm output port
A+ B- SGND: RS485 communication port
N: not connected pin
The controller includes four types of working modes: operating mode, parameter mode, manual operating mode, and query mode.
(1) Operating Mode:
The mode is normal working mode. There are three operating interfaces which can be selected. The three interfaces display different content. When they are not selected, the interfaces will automatically shift. Press the button “PgDn” to select next display interface; press the button “PgUp” to select the previous display interface.
Line 1: temperature and humidity inside the thermostatic box (or area I);
Line 2: box air conditioner status, real time clock;
------- cooling start sign;
------- heating start sign;
------- hydrogen exhaust /direct ventilation sign;
-- ------- compressor/ heater stop working.
Line 1: environment (or area II) temperature and humidity;
Line 2: inside and outside coil temperature display (T3, T4);
Circularly display current alarms;
When multiple alarms occur, it will display each alarm information circularly.
(2) Parameter Mode:
(a) Observation Parameter
(b) Control Parameter Revision
(c) Basic Parameter Revision
(d) Manual Operation
(e) Event Query
(f) Return To Operating Mode
a. Check operating parameters of key parts inside air conditioner, namely observation parameter. Operation steps:
Observation Parameter: on the left of line 1 is Parameter No. (PAnn); on the right of line 1 is parameter value. Line 2 shows the remark of the parameter.
b. Revise operating parameters of air conditioner, namely control parameters. Operation steps:
Control Parameter: on the left of line 1 is Parameter No. (PCnn), on the right of line 1 is parameter value. Line 2 shows the remark of the parameter.
c. Revise basic parameters of air conditioner. Operation steps:
Basic Parameter: on the left of line 1 is Parameter No. (PBnn), on the right of line 1 is parameter value. Line 2 shows the remark of the parameter.
(3) Manual Operation Mode:
Enter the interface to select “Cool” (cooing), “Heater” (heating), “Air” (direct ventilation) to conduct manual start (ON) and stop (OFF) operation.
(4) Event Query Mode:
9. Packing and Shipping
Our Delivery Agent
The goods can be shipped by sea, by air, by courier, by land, by train, etc.
Besides the following delivery agent, we can also look for the delivery agent with the best price in china if you need us to do for you.
10. Our Contact Information
Mobile Phone: 0086-13752765943
Telephone: 0086-0755 66600941
Contact Person: Fiona Liang
Tel: 86-13752765943 / 86-0755 23592644