Payment & Shipping Terms:
|Type:||Outdoor Cabinet Air Conditioner||Mounting Method:||Embedded|
|Ingress Protection:||IP55||Input Voltage Range:||-48VDC|
|Cooling Capacity L35/L35:||1500W||Power Consumption:||425W|
1500W Electrical Enclosure Air Conditioner,
IP55 Electrical Enclosure Air Conditioner,
48VDC outdoor enclosure air conditioner
48VDC IP55 1500W Electrical Enclosure Air Conditioner Energy Saving Remote
* Remote measuring, remote communication, remote control, which can realize multiple
automatic protection and comprehensive self-testing function;
* DC Air conditioner, Power supply voltage range;
* Fit for harsh condition (T3), R134a refrigerant ;
* Low power consumption design with (SEER≥5.5);
* LED display, all the settings can changed at the field;
* Strict process control and international brand parts deployed to ensure high quality and
* Dry contact alarm output, NO/NC optional, linkage function optional;
* Anti-theft design, without the protection cover.
2. Technical Parameter
|Dimensions (Include flange)||782*482*200||mm|
|Cooling capacity L35/L35||1500||W|
|Power consumption L35/L35||425||W|
|IP grade||IP 55|
3. Performace Curve
4. Air conditioner drawing
◊ In order to avoid short circuit of air duct, it is suggested to make effective isolation between inner air inlet and outlet.
P.S. This product is free of cover, customers don’t need to install additional cover.
1. If the customer needs to install a protective cover, in order to ensure enough circulation of air, the opening rate of the air inlet and outlet should be greater than 60%. It is very important to prolong the unit life and reduce the maintenance frequency.
2. The air inlet and outlet of the protective cover should prevent short circuit of air duct, so that the air-con can get the best cooling effect.
3. Due to the opening of the housing problems caused by.
6. Air conditioner picture
Contact Person: Merry Liang