IP55 Galvanized Steel Outdoor Telecom Cabinet With Front & Rear Access
1. Cabinet Features
1.1 External Dimension is W×D×H 750×750×1500mm
1.2 Galvanized steel,single wall with heat insulation
1.3 Anti-theft three point lock
1.4 The cabinet includes 19” standard installation rack.
1.5 The cabinet cooling uses 2 air conditioners and 2 fans.
1.6 Including -48VDC illumination lamp.
1.7 The layout of the cabinet is reasonable, which will facilitate cable access, fixing and grounding.
1.8At the bottom of the cabinet, there are entrance holes individually for power cable, signal cable and optical cable.
1.9 The cabinet is dustproof, sunproof and rainproof, which is used in outdoor environment.
1.10 All the cables, sealing and heat insulation used in the cabinet are made from flame retardant materials, which comply with GB5169.7 test A
1.11 IP55 protection level.
2. Cabinet Parameters
External Dimension W×D×H 750×750×1500mm
|Equipment Installation Method||19” standard rack,27U|
|Door||With one front door and one back door; with three point lock for outdoor cabinet (support padlock)|
Galvanized steel,single wall with heat insulation
|Temperature Control||Cooling||Air conditioners and fans|
|Lighting||LED lamp||48V LED lamp|
|Temperature||Temperature||Working Temperature: -40°C ~ +55°C|
|Storage Temperature: -50°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~ 100%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1124 × (1±5%)W/m2|
3. Components Installation
3.1 Environment Monitoring Unit is installed on 19" rack.LED lamp, smoke sensor and door sensor are installed at the top of the enclosure.
3.2 PDU is installed on 19” rack.
Class B lightning protection: 60KA*1;
AC Input: 63A/2P*1;
AC Output: 16A/1P*4;
DC Output: 16A/1P*4;
Input Voltage: AC220V 50Hz.
3.3 The cabinet cooling uses 2 air conditioners and 2 fans.
The air conditoners are installed in the front door and rear door.
The fans are installed on the top cover.
4. Cable Inlet
All feeder cable and other external cables all use bottom wiring method.
5. Cabinet Package
Wooden case with pallets