Payment & Shipping Terms:
|Dimension:||W×D×H 625×300×700mm||Material:||Galvanized Steel|
|Temperature Control:||DC48V Air Conditioner||Door Type:||With One Front Door|
telecom equipment cabinet,
outdoor telecom enclosure
13U Pole Mount Air Conditioner Cooling Outdoor Telecom Cabinet With One Front Door
This Pole Mounted Outdoor Telecom Cabinet is widely used in wireless communication base station, such as 4G system, communication/network integrated service, access/transmission switching station, emergency communication/transmission, etc.
External Size:W×D×H 625×300×700mm
|Equipment Installation Method||19” standard rack|
|Door||With one front door, and anti-theft three point lock for outdoor cabinet (support padlock)|
|Material||Galvanized steel; double walls, thickness of outer plate: 1.5mm, thickness of inner plate: 0.5mm, with 20mm PEF heat insulation between two walls.|
|Temperature Control||Cooling||DC48V air conditioner|
|Lighting||LED lamp||48V LED lamp|
|Temperature||Temperature||Working Temperature: -20°C ~ 55°C|
|Storage Temperature: -40°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~ 100%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1124 × (1±5%)W/m2|
3. Cabinet Features
3.1 Applicable environment conditions:
Environment temperature: -40°C ~ + 70°C;Environment humidity (RH): ≤95% (at + 40°C);Air pressure: 62kPa ~ 102kPa.
3.2 Material: galvanized steel.
3.3 Surface treatment: degreasing, derusting, rustproof phosphating (or galvanizing), powder coated.
3.4 Ingress protection: IP55.
3.5 Flame retardance: comply with GB5169.7 test A.
3.6 Insulation resistance: the insulation resistance between grounding devices and cabinet body parts is not lower than 2X104M/500V(DC).
3.7 Withstand voltage: the withstand voltage between grounding devices and cabinet body parts is not lower than 3000V(DC)/1min.
3.8 Mechanical strength: each surface can bear upright pressure＞980N; after the door is open, its outer end can bear upright pressure ＞200N.
4. Cable Entrance
All outside cables use bottom entrance method.
6.Theft Proof Design
6.1 Door lock theft proof design
(1) Damage resistance of the theft proof lock meets GA/T 73-1994 “Mechanical Anti-theft Lock” class B requirement, supporting padlock.
(2) Three point lock
6.2 Connection and Fastening
(1) Use anti-loose threaded connection as structure and bearer connection. Anchor bolt for fixing cabinet use hot dip galvanized bolts.
(2) Door hinges use inner hinge mode.
6.3 Appearance and Surface Treatment
Cabinet surface coating is outdoor special powder coating, with white gray color (PANTONE 428C). The coating complies with GB/T 3181-2008 requirement.
Contact Person: Fiona