Payment & Shipping Terms:
|Ingress Protection:||IP55||Input Voltage:||AC220V±15% 50Hz|
|Cooling Capacity L35/L35:||400W||Heating Capacity:||300W|
electrical enclosure air conditioner,
outdoor enclosure air conditioner,
Remote Monitor Kiosk Air Conditioner
Kiosk Air Conditioner 220VAC 400W Cooling Capacity With 300W Heating Capacity
1. Product Parameters
|Dimensions(Without flange)||HWD 470*450*158mm|
|Mounting method||Door mounted|
|Working temperature||-40℃ -55 ℃|
|Input voltage||220 VAC±15% ～/50Hz|
|Cooling capacity L35/L35||400 W|
Rated Refrigerating input
|Rated Refrigerating current (L35/L35)||1.1A|
|IP grade||IP 55|
2. Preparation And Installation
2.1 Removing package and checking
1. Please prepare installation tools: knife and scissors, and wear protective gloves.
2. Please remove wrapping film and packing belt, then remove the carton, take out the air
3. Please check the attachment list and accessory bags in the carton, check whether the air conditioner model is right .
2.2 Mechanical installation
Installation tool: Phillips screwdriver
1) Choose cut location on the cabinet according to the holing diagram, remove the shadow area and make the installation hole.
2) Make air conditioner flange close to cabinet door, Fix the air conditioner on the installation surface of the cabinet firmly with M5 screws.
3) Check whether air conditioner is installed levelly and firmly.
3 Product function
When the temperature inside cabinet is higher than refrigeration starting temperature, it starts
refrigerating; when the temperature inside cabinet is lower than refrigeration stopping temperature, it
When the temperature inside cabinet is lower than heating starting temperature, it starts heating;when the temperature inside cabinet is higher than heating stopping temperature, it stops heating.
3.3 Remote monitor
Air conditioner has an RS485 communication interface, supporting MODBUS- RTU communication protocol.The air conditioner communicates with the upper monitor through the RS485 communication interface. Or users can check the air conditioner’s running state by viewing the display screen directly and change its running parameters.
3.4 The control of external fan (Optional)
According to the optional requirement, the external fan (Hydrogen discharge / emergency fan) automatically realizes cycle hydrogen discharging and emergency ventilation function.
Hydrogen discharge function(Optional):When hydrogen discharge cycle comes, air conditioner start the hydrogen discharge fan, the control switch closes.
Emergency ventilation function (Optional): When the temperature inside cabinet is higher than Emergency ventilation starting temperature, emergency ventilation fans run; when the temperature inside cabinet is lower than Emergency ventilation stopping temperature, emergency ventilation fans stop.
4. Product Pictures
Contact Person: Fiona Liang
Tel: 86-13752765943 / 86-0755 23592644