Payment & Shipping Terms:
|External Dimension:||W×D×H 900×900×2100mm||Internal Dimension:||W×D×H 800×800×1800mm|
|Ingress Protection:||IP55||Cooling:||Air Conditioner And Fans|
Galvanized Steel Outdoor Equipment Enclosure,
2100mm Outdoor Equipment Enclosure,
2100mm outdoor electronics cabinet
2100mm Galvanized Steel Outdoor Equipment Enclosure Double Door
10 years of experience in the design and fabrication of electrical enclosures that provide custom solutions at standard-model budgets. Our innovative electrical enclosure designs allow for efficient, cost-effective customization, ensuring that your enclosure meets your product and budget requirements. We are committed to meeting the fast turnarounds and cost-savings you need.
● Cooling by air conditioner
● High integration, compact structure, easy installation and migration on later stage
● Anti-theft three point lock
● Full protection: door sensor, smoke sensor, water sensor, temperature & humidity sensor. Environmental monitoring system provides alarm.
● Material: galvanized steel or as customer's requirements
3. Technical Parameters
External Dimension: W×D×H 900×900×2100mm
Internal Dimension: W×D×H 800×800×1800mm (19” 40U)
|Equipment Installation Method||19” rack|
|Door||With one front door and one back door, and anti-theft three point lock for outdoor cabinet (support padlock).|
|Material||Galvanized steel, double wall with insulation|
|Temperature Control||Cooling||air conditioner and fans|
|Lighting||LED lamp||48V LED lamps|
|Temperature||Temperature||Working Temperature: -40°C ~ +55°C|
|Storage Temperature: -50°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~ 100%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1120 ×(1±5%)W/m2|
4. Accessories List
|1||Outdoor Telecom Cabinet||1||PC||
(1) External Dimension: W×D×H 900×900×2100mm
Internal Dimension: W×D×H 800×800×1800mm
(2) One compartment: 19” 40U
(3) With one front door and one back door, and anti-theft three point lock for outdoor cabinet (support padlock).
Cooling capacity: 1.5KW.
Power Supply: AC220V, 50Hz.
One installed on front door, the other on back door.
|3||Auxiliary Direct Ventilation Fans||2||PC||DC48V|
|4||Environment Monitoring Unit||1||PC||1U, DC48V, support SNMP communication|
|7||Temperature and Humidity Sensor||1||PC|
|11||LED Lamp Switch||2||PC||One for controlling LED lamp on/off|
|12||Power Distribution Unit||1||PC||
Grade B Lightning Proof AC Input: 63A/2P×1; AC Output: 16A/1P×4;
DC Output: 16A/1P×4
Input Voltage: AC220V, 50Hz
5. Cabinet Dimensions
6. Cabinet Pictures
7. Power system connections
Communication cable making
Definition: Put the side with plastic shell of registered jack down, and the side with PIN up; put the end with PIN away from you, and the end with square hole near you (the end for pushing the network cable in when making network cable). Then define the far left one as PIN1, and the far right one as PIN8.
b. For RS232communication, PIN1 is 232TX (send), PIN4 is 232RX(receive), PIN5 is communication grounding.
c. For RS485 communication, PIN2 is RS485+, PIN3 is RS485-, other PINs are suspended.
d. Ethernet communication cable adopts T568A standard and T568B standard.
e. T568A standard cable connection method is from left to right: green and white--green--orange and white- -blue--blue and white--orange--brown and white--brown.
f. T568B standard cable connection method is from left to right: orange and white--orange--green and white- -blue--blue and white--green--brown and white--brown.
g. When two ends of the Ethernet cable both adopt T568A standard or T568B standard, it is Ethernet direct cable; When one end adopts T568A standard while the other end adopts T568B, it is Ethernet cross cable.
Contact Person: Fiona Liang
Tel: 86-13752765943 / 86-0755 23592644