Payment & Shipping Terms:
|Cooling:||AC110V 60Hz 600W Air Conditioner And DC48V Fans||External Dimension:||H×W×D 1100×650×500mm|
|Material:||Double Wall Galvanized Steel,with Heat Insulation||Installation Method:||Pole Mounted And Floor Mounted|
|Surface Treatment:||Anticrossive Powder Coating||Working Temperature:||-20°C ~ 55°C|
|Lock:||Anti-theft Three Point Lock||Relative Humidity(RH):||5% ~ 100%|
|Solar Radiation Intensity:||1124 × (1±5%)W/m2||Color:||Green|
outdoor pole mount enclosure,
outdoor electronics cabinet
18U Standard 19” Rail Outdoor Telecom Cabinet / Enclosure Pole and Floor Mounted With Air Conditioner
(1) Technical Parameters
|Structure||Dimension||External Dimension H*W*D 1100×650×500mm|
|Equipment Installation Method||19” standard rack|
|Door||With one front door, and anti-theft three point lock for outdoor cabinet (support padlock)|
2.Double wall, thickness of outer plate: 1.5mm, thickness of inner plate: 0.8mm, with 20mm heat insulation between two walls.
3. Anti-corrosion powder coating
|Temperature Control||Cooling||AC110V 60Hz 600W air conditioner and DC48V fans|
|Lightning Proof||Grade B lightning proof||Nominal: 60KA, Max.: 100KA|
|Lighting||LED lamp||48V LED lamp|
|Temperature||Temperature||Working Temperature: -20°C ~ 55°C|
|Storage Temperature: -40°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~ 100%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1124 × (1±5%)W/m2|
(2) Accessories List
|1||Outdoor Telecom Cabinet||1||Set||
(1)External Dimension H×W×D 1100×650×500mm
(2) One compartment;
(3) With one front door, and anti-theft three point lock for outdoor cabinet (support padlock)
(4) Material: galvanized steel; double walls, thickness of outer plate: 1.5mm, thickness of inner plate: 0.8mm, with 20mm PEF heat insulation between two walls.
(5) Installation method: pole mount & floor mount, including installation accessories
Cooling Capacity: 600W
Power Supply: AC110V 60Hz
|3||Fan||2||PC||DC48V, on the top|
|5||Door Sensor||1||PC||Used for controlling LED lamp on/off|
The ET6550110-PF Pole and floor Mounted Outdoor Telecom Cabinet is widely used in wireless communication base station, such as 4G system, communication/network integrated service, access/transmission switching station, emergency communication/transmission, etc.
4.1 The cabinet is dustproof, sunproof and rainproof, which is used in outdoor environment.
4.2 The cabinet use air conditioner and fans for cooling.
4.3 The cabinet includes -48VDC LED lamp for illumination.
4.4 The layout of the cabinet is reasonable, which will facilitate cable access, fixing and grounding. There’re cable entrance holes individually for power cable, signal cable and optical cable at the bottom of cabinet.
4.5 All the cables, seal and insulation material used in the cabinet are made from flame retardant materials.
4.6 The cabinet use standard 19” rack installation method.
5.1 Applicable environment conditions:
Environment temperature: -40°C ~ + 70°C;
Environment humidity (RH): ≤95% (at + 40°C);
Air pressure: 62kPa ~ 102kPa.
5.2 Material: galvanized steel.
5.3 Surface treatment: degreasing, derusting, rustproof phosphating (or galvanizing), powder coated.
5.4 Cabinet load bearing: ≥300kg.
5.5 Ingress protection: IP55.
5.6 Flame retardance: comply with GB5169.7 test A.
5.7 Insulation resistance: the insulation resistance between grounding devices and cabinet body parts is not lower than 2X104M/500V(DC).
5.8 Withstand voltage: the withstand voltage between grounding devices and cabinet body parts is not lower than 3000V(DC)/1min.
5.9 Mechanical strength: each surface can bear upright pressure＞980N; after the door is open, its outer end can bear upright pressure ＞200N.
Cabinet External Size : W×D×H: 650×500×1100mm (19”,18U)
LED illumination lamp, door sensor, fans are installed at the top part of the cabinet.
All outside cables use bottom entrance method.
(1) The cabinet includes grounding copper bar with anti-corrosion coating. There are enough screws for wiring connection terminals.
(2) The metal part of the cabinet should be interconnected and be connected with grounding bar. Connection resistance between any two points is lower than 0.1Ω.
class B requirement, supporting padlock.
(2) Three point lock
(1) Use anti-loose threaded connection as structure and bearer connection. Anchor bolt for fixing cabinet use hot dip galvanized bolts.
(2) Door hinges use inner hinge mode.
Cabinet surface coating is outdoor special powder coating, with green color. The coating complies with GB/T 3181-2008 requirement.
Contact Person: Fiona Liang
Tel: 86-13752765943 / 86-0755 23592644