Payment & Shipping Terms:
|Mounting Method:||Embeded||Input Voltage:||AC 110V±15% 50/60Hz|
|Cooling Capacity L35/L35:||500 W||Ingress Protection:||IP55|
outdoor enclosure air conditioner,
control cabinet air conditioner
IP55 Electrical Enclosure Air Conditioner 110VAC 500W For Outdoor Telecom Enclosure
1. Key Features
Remote measuring, remote communication, remote control, which can realize multiple automatic protec-tion and comprehensive self-testing function;
Strict process control and famous brand components to ensure high quality and reliability of this prod-uct;
Fit for harsh condition (T3), R134a refrigerant ;
Multiple self-protection design , RS485 communication port (MODBUS-RTU protocol);
Built-in condensate water evaporating device is optional;
LED display, all the settings can changed at the field;
The heating function is optional;
Dry contact alarm output, NO/NC optional;
The product is widely used in outdoor communication cabinets, electrical cabinets, industrial cabinets and other occasions need heat dissipation. Create a cool, dry and safe environment for the operation of equipment and electrical enclosure
|Dimensions (Include flange)||582*352*175mm|
|Application temperature||-40℃ -70 ℃|
|Working temperature||-15℃ -55 ℃|
|Input voltage||AC 110V±15% 50/60Hz|
|Cooling capacity L35/L35||500 W|
|Power consumption L35/L35||270 W|
|IP grade||IP 55|
4. Installation instructions
In order to avoid short circuit of air duct, it is suggested to make effective isolation between inner air inlet and outlet.
This product is free of cover, customers don’t need to install additional cover.
1. If the customer needs to in-stall a protective cover, in order to ensure enough circulation of air, the opening rate of the air inlet and outlet should be greater than 60%. It is very important to prolong the unit life and reduce the maintenance frequency.
2. The air inlet and outlet of the protective cover should pre-vent short circuit of air duct, so that the air-con can get the best cooling effect.
Contact Person: Fiona