Payment & Shipping Terms:
|Working Voltage:||AC9V～35V||Working Temperature:||-10℃～+50℃|
|Alarm Output:||Normally Open/normally Closed Optional, Contact Capacity DC28V 100mA||Alarm Indication:||Red LED Always On|
environmental monitoring devices,
environmental monitoring unit
Non Coding Photoeleciric Smoke Detector AC9V - 35V Working Voltage
1. Prodcut Instruction
The product is a non coding smoke detector, with a pair of switch output contacts, which can choose the normally open and normally closed output according to the actual needs. In normal operation, the indicator light flashes every 8 seconds; in alarm, the indicator light is always on, and the alarm output contact acts at the same time.
2. Product Features
3. Technical Parameters
|Standby current||16mA(Relay normally closed) 3mA(Relay normally open)|
|Alarm current||8mA(Relay normally closed) 19mA(Relay normally open)|
|Alarm indication||Red LED always on|
|Sensor||Infrared photoelectric sensor|
|Environment temperature||Max.95﹪RH(no condensation)|
|Anti RF interference||10MHz—1GHz 20V/m|
Normally open/normally closed optional, contact capacity DC28V 100mA
|Reset mode||Automatic reset / power off reset optional|
|Coverage area||When the space height is 6m-12m, the protection area of a detector is 80 square meter for general protection site; when the space height is below 6m, the protection area is 60 square meter. The specific parameters shall be subject to the code for design of automatic fire alarm system GB50116-98.|
4. Product installation
4.1 Select the appropriate installation location, generally installed on the ceiling in the center of the detector coverage area.
4.2 Connect the power line and signal line to the mounting base(mounting base〝1〞and〝2〞are no polarity input for power supply;〝3〞and〝4〞are alarm output contact)
4.3 Description of blue two digit dip switch
"2" corresponds to KT control switch
"1" corresponds to RST control switch
4.3.1 KT alarm output setting
When the KT switch "2" is pulled to the letter "on", the relay is normally closed
When the KT switch "2" is pulled to the letter "off", the relay is normally open
4.3.2 RST alarm mode
When RST switch "1" is pulled to the letter "on", it will reset automatically.
When RST switch "1" is pulled to the letter "off", the power is cut off and reset
4.4 Screw the mounting base to the ceiling
4.5 Align the locating convex point at the base end of the detector with the locating groove of the mounting base, and rotate clockwise to install the detector.
5.1 Pay attention to dust prevention. The dust cover must be removed after the project is officially put into use.
5.2 There shall be no shelter within 0.5m around the detector.
5.3 The horizontal distance between the detector and the air supply hole of the air conditioner shall not be less than 1.5m.
5.4 The horizontal distance between detector and wall, beam edge shall not be less than 0.5m.
5.5 The detector shall be installed in the middle of the inner walkway ceiling with a width of less than 3m. The installation spacing of the detector shall not exceed 15m, and the distance between the detector and the end wall shall not be greater than half of the installation spacing of the control detector.
5.6 The detector should be installed horizontally. For example, the inclination angle of inclined installation should not be greater than 45 degree.
5.7 The detector base shall be installed firmly and its wire connection must be reliable.
5.8 It is recommended to conduct a simulated fire test once half a year to test whether the detector works normally.
6. Package Pictures
Contact Person: Fiona Liang
Tel: 86-13752765943 / 86-0755 23592644