Payment & Shipping Terms:
|External Dimension:||W×D×H 750×700×2000mm (38U 19" Rack)||Material:||Stainless Steel|
|Color:||Anti-corrosion Outdoor Powder Coating Grey RAL7032||Protection Grade:||IP55|
|Grounding Protection:||Copper Bar||Cooling:||DC48V 2000W Air Conditioner And DC48V Fans|
|Working Temperature:||-40°C ~ +55°C||Cabinet Lock:||Anti-theft Three Point Lock|
|Structure:||Assembled, Single Layer Stainless Steel +heat Insulation Cotton||Roof:||Removable|
Single Wall Heat Insulation 38U Outdoor Telecom Enclosure 750x700x2000 With DC Air Conditioner
Single Wall Stainless Steel Heat Insulation 38U Outdoor Telecom Cabinet 750x700x2000 With DC Air Conditioner
1. Application Scope
The ET7570200 Outdoor Telecom Cabinet is mainly used in communication base station, such as 4G
system, communication/network integrated service, access/transmission switching station, emergency
2. Cabinet Introduction
2.1 Cabinet Material
The cabinet is made of stainless steel.
(1) For front door, roof, two side panels and back panel: outer wall is 1.6mm stainless steel 304, inner wall
is 20mm PEF heat insulation.
(2) Plinth: outer wall is 2.0mm stainless steel 304, inner wall is 20mm PEF heat insulation.
The cabinet is assembled type.
2.2 Cabinet Structure
The cabinet includes one compartment,there is 19” rack form up to down, 38U space.
2.3 Cabinet Door and Lock
The door opening angle is larger than 110°and the door limit device can limit the opening angle. The lock
is theftproof three point lock, supporting padlock.
3.1 The cabinet is dustproof, sunproof and rainproof, which is used in outdoor environment.
3.2 The cabinet cooling use one air conditioner, which work in alternation to continuously keep
thermostatic inside the cabinet.
3.3 The layout of the cabinet is reasonable, which will facilitate cable access, fixing and grounding. On the
back of the cabinet, there are entrance holes individually for power cable, signal cable and optical cable.
3.4 All the cables, sealing and heat insulation used in the cabinet are made from flame retardant
3.5 The cabinet uses assembled structure, easy for installation.
3.6 The cabinet includes 19” standard installation rack.
4. Technical Specs
(1) Applicable environment conditions:
Environment temperature: -40°C ~ + 70°C
Environment humidity (RH): ≤95% (at + 40°C)
Air pressure: 62kPa ~ 102kPa
(2)Material: quality stainless steel
(3)Surface treatment: degreasing, derusting, rustproof phosphating (or galvanizing), powder coated.
(4)Cabinet load bearing: ≥600kg
(5)Ingress protection: IP55
(6)Flame retardance: comply with GB5169.7 test A
(7)Insulation resistance: the insulation resistance between grounding devices and cabinet body parts is
not lower than 2X104M/500V(DC).
(8)Withstand voltage: the withstand voltage between grounding devices and cabinet body parts is not
lower than 3000V(DC)/1min.
(9)Mechanical strength: each surface can bear upright pressure＞980N; after the door is open, its outer
end can bear upright pressure ＞200N.
(10)Technical Parameters List
|Structure||Dimension||External Size W×D×H 750×700×2000mm|
|Equipment Installation Method||19” standard rack|
|Door||With one front door ,and anti-theft three point lock for outdoor cabinet (support padlock)|
Single layer stainless steel + heat insulation :
Front door, roof, two side panels and back panel: outer wall is 1.6mm stainless steel 304, inner wall is 20mm PEF heat insulation.
Plinth: outer wall is 2.0mm stainless steel 304, inner wall is 20mm PEF heat insulation.
|Coating||Anti-corrosion outdoor powder coating grey RAL7032|
|Temperature Control||Cooling||DC48V Air Conditioner and fans|
|Lighting||LED lamp||48V LED lamp|
|Temperature||Temperature||Working Temperature: -40°C ~ +55°C|
|Storage Temperature: -50°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~ 100%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1124 × (1±5%)W/m2|
(11) Accessories List
|1||Outdoor Telecom Cabinet||1||Set||
(1)38U 19" rack
(2)With one front door, and anti-theft three point lock(support padlock)
(3)Grounding Protection: copper bar at the bottom of the cabinet
(4)Including cable entry on the back, including 10 glands, besides, we configure extra 12 glands packed in the cabinet
(5) 25 mm² DC cable, packed in the cabinet.
(6) Installation bolts of plinth, packed in the cabinet
Cooling Capacity: 2000W;
Power Supply: DC48V
On the front door
|3||Fan||2||Set||DC48V, on the front door, used for the back up of air conditioner|
|4||Power Distribution Unit||1||Set||
(1)One 100A incomer breaker as isolater
(2)DC bus bar
(3)Two units of DC distribution boxes, serve as 1+1 for the trasmission equipment, each box contain the followong load breaker, used for connecting to DC48V air conditioner and radio euquipment.
(2) Capacity: 16 system
(3) Size: H×W×D 110×485×95mm
(4) Connection method: SIEMENS mode
(5) Including cable and related accessories, cable head specifications: 75-2-1
|6||Environment Monitoring System||1||Set||
1* environment monitoring unit;
1* smoke sensor;
1* water sensor;
1* temperature&humidity sensor;
1* tilt &shock combination sensor;
1* door sensor
power supply: DC48V
Communication Protocol: RS485 and SNMP
|7||LED Lamp Sensor||1||Set||Used for Controlling LED lamp on/off|
Cabinet External Dimension (W×D×H):750×700×2000mm (excluding air conditioner)
5.Main Electrical Components
5.1 DC48V 2000W air conditioner and 2 fans are installed on the front door. The fans function is the backup of air conditioner, the fans only start to work in the event of air conditioner failure. The fans will be closed when the air conditioner is in operation.
5.2 PDU, Environment Monitoring Unit and DDF are installed on the 19” rack.
5.3 LED illumination lamp, LED Lamp sensor, door sensor, smoke sensor and tilt & shock sensor are on top of the cabinet.
5.4 The water sensor is at the bottom of the cabinet.
5.5 The temperature & humidity sensor is on the side panel
6. Wire Routing Design
Feeder cable and other external cables all use back wiring method.
7. Grounding Protection
(1)The cabinet includes grounding copper bar with anti-corrosion coating, with 120mm2 sectional area.
There are enough screws for wiring connection terminals.
(2)The metal part of the cabinet should be interconnected and be connected with grounding bar.
Connection resistance between any two points is lower than 0.1Ω.
(3)Protective earthing of other equipments inside the cabinet should be connected to the grounding bar.
8. Theft Proof Design
8.1 Door lock theft proof design
(1)Damage resistance of the theft proof lock meets GA/T 73-1994 “Mechanical Anti-theft Lock” class B
requirement, supporting padlock.
(2)Three point lock
8.2 Connection and Fastening
(1)Use anti-loose threaded connection as structure and bearer connection. Anchor bolt for fixing cabinet
use hot dip galvanized bolts.
(2)Door hinges use inner hinge mode.
8.3 Appearance and Surface Treatment
Cabinet surface coating is outdoor special powder coating, with gray color (PANTONE 428C). The coating
complies with GB/T 3181-2008 requirement.
8.4 Door Limit
(1) Cabinet door options: vertical hinge door, horizontal hinge door.
(2) The door limit device can limit the door position when it is open.
(3) The door limit function is automatically activated when the door is open, and should be canceled
manually when the door is closed
(4)When the door is fully opened, the largest open angle is larger than 95°. If it is horizontal hinge door, it
can prevent outside water from flowing into the equipment compartment from the upper side. The bottom
edge of the door limit device is higher than the hinge level, which can offer enough operating space.
(5) After 1000 times open and close operation, the door and door device will have good function and have
no excessive wear and tear.
(6) At the door limit status, the door limit device can bear the static load by door opening and closing at
22m/s wind, without mechanical failure and function failure.
There are 12 pcs of screws on the cabinet roof, as shown below picture. Unscrew the screws from the
inside roof, then the roof can be removed, the diagram is as below.
Notes: inside the top, 3 pcs of srews on left side and 3 pcs of srews on right side are concealed by the
inner side insulation cotton. The insulation cotton is required to be folded down a little, then the screw can
Besides, the roof has ventilation hole, as shown below picture
10. Cabinet Installation
10.1 Position of installation hole at cabinet base is as the following diagram.
10.2 Use 8 pcs of M16 bolts to fasten the cabinet on the existing base,(such as concrete base)
10.3 According to site situation, put the cabinet on the concrete base with forklift, crane or manually, and
fix it on the concrete base with bolts.