Payment & Shipping Terms:
|Cable Entry:||From Cabinet Bottom||Material:||Galvanized Steel|
|Cabinet Lock:||Anti-theft Three Point Lock||External Dimension:||H×W×D 1800×1000×1000mm|
|Doors:||Two||Illumination:||DC48V LED Lamp|
|Cooling:||DC48V 500W Air Conditioner|
IP65 19” Outdoor Telecom Equipment Cabinet With DC48V Cooling System / Customized Metal Outdoor Telecom Cabinet
|Place of Origin: Shenzhen, China (Mainland)||External Size H×W×D 1800×1000×1000mm|
Brand Name: ESTEL
|Structure: double wall, with insulation, sandwich structure|
Model Number: ET100100180B
|Cabinet Layout: one compartment, for installing 19” equipment|
Product Name: Outdoor Telecom Equipment Cabinet
|Cabinet Lock: anti-theft three point lock|
|Certification: ISO9001, CE, 3C, FCC, TLC, IP55||
Protection Level: IP65
|Application: outdoor telecom base station||Cable Entry: at cabinet bottom|
|Material: galvanized steel||Illumination: DC48V LED lamp|
Heat Insulation: PEF
|Grounding Protection: copper bar|
Color: grey (support custom made)
|Cooling: DC48V 500W air conditioner|
Coating: anti-corrosion outdoor powder coating
|Accessories Options: PDU,environment monitoring system|
Payment & Shipping Terms
|Minimum Order Quantity:||1 set|
|Payment Terms:||L/C,D/A,T/T, Western Union, Paypal, etc|
|Supply Ability:||7,200 sets per month|
|Delivery Time:||15-20 working days|
|Packaging Details:||wooden case|
(1) Technical Parameters
|Structure||Dimension||External Dimension H×W×D 1800×1000×1000mm|
|Equipment Installation Method||19” standard rack|
With one front door and one back door, totally two doors;
with anti-theft three point lock for outdoor cabinet (support padlock)
2.double walls, thickness of outer plate: 1.5mm, thickness of inner plate: 0.8mm, with heat insulation between two walls.
DC48V 500W air conditioner
|Lighting||LED lamp||48V LED lamp|
|Temperature||Temperature||Working Temperature: -40°C ~ +55°C|
|Storage Temperature: -50°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~99%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1124 × (1±5%)W/m2|
(2) Accessories List
|1||Outdoor Telecom Cabinet||1||Set||
(1) External Size H×W×D 1800×1000×1000mm
(2) One compartment;
(3) With one front door and one back door, totally two doors; with anti-theft three point lock for outdoor cabinet (support padlock)
(4) Material: galvanized steel; double walls, thickness of outer plate: 1.5mm, thickness of inner plate: 0.8mm, with heat insulation between two walls.
Power Supply: DC48V
|3||Power Distribution Unit||1||Set||
Grade B Lightning Proof
AC Input: 63A/2P *1;
AC Output: 16A/1P*4;
DC Output: 16A/1P*4.
|4||Environment Monitoring System||1||Set||
1× environment monitoring unit, with TCP/IP communication port;
1× water sensor;
1× smoke sensor;
1× temperature and humidity sensor;
2× door sensor
The Outdoor Telecom Cabinet is mainly used in communication base station, such as 4G system, communication/network integrated service, access/transmission switching station, emergency communication/transmission, etc.
The cabinet is made of galvanized steel, with double walls, thickness of outer plate: 1.5mm, thickness of inner plate: 0.8mm. There are heat insulation between inner wall and outer wall. The insulation material is 40mm PEF, heat insulation coefficient: 0.035W/m·K. The cabinet is assembled type.
The cabinet includes 19” equipment installation rack. The cabinet includes two air conditioners, one installed on front door and another installed on back door.
The cabinet includes one front door and one back door. The cabinet door uses embedded structure. The door opening angle is larger than 110°and the door limit device can limit the opening angle. The lock is theftproof three point lock, supporting padlock. Each cabinet door include open door sensor, working together with the environment monitoring unit.
4.1 The cabinet is dustproof, sunproof and rainproof, which is used in outdoor environment.
4.2 The cabinet cooling uses air conditioner.
4.3 Including -48VDC illumination LED lamp.
4.4 The cabinet includes power and environment monitoring unit, which can send power failure alarm, door open alarm, temperature and humidity alarm, smoke alarm, water alarm etc.
4.5 The layout of the cabinet is reasonable, which will facilitate cable access, fixing and grounding. At the bottom of the cabinet, there are cable inlets separately for power cable, signal cable and optical cable.
4.6 All the cables, sealing and heat insulation used in the cabinet are made from flame retardant materials.
4.7 The cabinet includes 19” standard installation rack.
Operating temperature: -40°C ~ + 55°C
Storage temperature: -50°C ~ + 70°C
Transport temperature: -50°C ~ + 70°C
Relative humidity (RH): 5%~99%
Air pressure: 62kPa ~ 101kPa (similar to 0m ~ 5000m altitude)
Cabinet External Dimension (W×D×H): 1000×1000×1800mm.
6.1 LED lamp, LED lamp sensor, smoke sensor, door sensor and temperature & humidity sensor are installed at the top of the cabinet.
6.2 Water sensor is installed at the bottom of the cabinet.
6.3 PDU and environment monitoring unit are installed on 19” rack.
6.4 The cabinet includes totally two air conditioners, one air conditioner installed on front door and the other installed on back door.
6.5 The cabinet includes rubber base plate, for installation on transport telecom tower trailer.
Feeder cable and other external cables all use bottom wiring method.
Cabinet surface coating is outdoor special powder coating, with white gray color (PANTONE 428C). The coating complies with GB/T 3181-2008 requirement.
10.1 Position of installation holes at cabinet base are as follows:
10.2 Users prefabricate concrete base.
10.3 Pre-embed 4pcs M10×120 anchor bolts on the concrete base. Distance between bolts are as that in diagram 1. Bolt exposed height is 40mm. Put the cabinet on the concrete base, align anchor bolts, then screw on nuts, and tighten them with wrench.
10.4 According to site situation, put the cabinet on the concrete base with forklift, crane or manually, and fix it on the concrete base with bolts.
(1) Compressor Air Conditioner.
Power Supply: DC48V.
Cooling Capacity: 500W.
Quantity: 2 pcs air conditioners for each cabinet, one installed on front door and the other installed on rear door.
(2) Working Principle: the cabinet includes auto switching controller for the two air conditioners. Air conditioner 1 is main air conditioner, and air conditioner 2 is backup air conditioner. Air conditioner 1 will keep working if there is no failure and alarm; only in case air conditioner 1 send failure alarm, air conditioner 2 will start to work, and air conditioner 1 will stop working.
13. Packing and Shipping
Contact Person: Fiona