Payment & Shipping Terms:
|Installation Mode:||Door Mounted||OEM:||Support|
|Cover Material:||Galvanized Steel||Application:||Outdoor Telecom Enclosure|
server cabinet air conditioner,
control cabinet air conditioner
DC48V 800W Variable Frequency Air Conditioning for Outdoor Battery Cabinet
|Place of Origin: Shenzhen, China||Rated Cooling Capacity : 800W|
|Brand Name: ESTEL||Dimension W×D×H: 482×187×781mm|
|Model Number: DCSAD-2(800W)||Input Voltage: DC48V, variable frequency|
|Product Name: DC48V Outdoor Cabinet Air Conditioner||Rated Input Power: 450W|
|Certification:ISO9001, CE, 3C, FCC, TLC||Working Temperature: -5°C ~ +55°C|
|Cover: including outer cover||Noise: ≤60dB|
|Color: gray||Refrigerant: R134a|
|Protection Level: IP55||Cooling Method: DC48V compressor, active cooling|
|Installation Mode: door mounted,side mounted||Support OEM|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 set|
|Payment Terms:||L/C,D/A,T/T, Western Union, Paypal, etc|
|Supply Ability:||10,000 sets per month|
|Delivery Time:||7-15 working days|
|Packaging Details:||carton + foam + wooden case +pallet|
Cabindet air conditioner is actively cooling with compressor, and it will remove the heat inside the cabinet to outside. It also can keep the dust and heat outside the cabinet, avoiding problems from using fan. The inside cabinet can be maintained at an ideal temperature (30ºC) for electrical components which effectively guarantees the stability of the electronic equipment and improves the reliability of the whole system.
(As Picture A)
1. This series of products can be widely used for outdoor communication cabinets, battery cabinets, electric cabinets and industry control cabinets etc.
2. The protective level of internal and external circulation is IP55, which can protect cabinet to avoid moisture, dust, water. The air conditioner can also be indoor or outdoor installed.
3. R134a system.
4. R134a system fits working conditions of high/low temperature 55 ºC /-5 ºC.
5. Digital temperature controller and high precision of temperature control.
1. The pictures are only for reference.
2. When installation, please put the side with display screen inside the cabinet, and the other side outside.
|Cooling Capacity (W)||800|
|Rated Power(L35/L35) (W)||450|
|Working Temperature (°C)||-5～55|
4.1 Basic Components
Air conditioner is composed of compressor, condenser, evaporator, electric control system, expansion valve and capillary tube, dry filter and fans etc.
4.2 Cooling Theory
4.2.1 The compressor takes in the gas refrigerant from the evaporator and compresses it into high temperature and high pressure then sends it into the condenser. The refrigerant will release heating in the condenser and then the cold high pressure liquid goes through capillary throttling and turns into low temperature and low pressure and then flows in to the evaporator. The refrigerant will absorb heat and then turns into gas in the evaporator. Thus forms the cooling cycle system.
4.2.2 The condenser and evaporator has circulation fan to enhance air convection and heat exchange efficiency. The heat exchange between condenser and air is outside the control box and that of evaporator and air is inside the control box.
4.2.3 The electrical system is mainly monitoring the temperature of the cooled closed cabinet and controls the cooling circulation by setting temperature.
4.2.4 Drawing of cooling theory.
5. Installation Drawing
6. Wiring Terminals
7. Electrical Schematics
8. Packing and Shipping
Our Delivery Agent
The goods can be shipped by sea, by air, by courier, by land, by train, etc.
Besides the following delivery agent, we can also look for the delivery agent with the best price in china if you need us to do for you.
9. Our Contact Information
Mobile Phone: 0086-13752765943
Telephone: 0086-0755 66600941
Contact Person: Fiona